Medium Voltage Outdoor Applications
Tridelta has a long tradition in the production of distribution arresters. Our first medium voltage arresters were produced in 1962.
The housing of these valve-type arresters was generally porcelain. Since 1996 our medium voltage arrester are made only using light and cost-effective silicone housing; they have passed the 5000h ageing test successfully.
Different creepage distance variants and a wide range of connectors and accessories allow customized solutions – please contact us!
|Product||SBK class 1||SBK class 2|
|Highest System Voltage Us||kV||72||72|
|max. Rated Voltage Ur||kV||60||60|
|max. Nominal Discharge Current In (at 8/20 µs waveshape)||kA||10||10|
|max. Thermal Energy Absorption Capability kJ per kV of Ur||4,5||4,5|
|max. Line Discharge Class||1||2|
|High Current Withstand Strength 4/10 µs||kA||100||100|
|max. low Current Withstand Strength 2 ms||A||500||500|
|max. Short Circuit / Pressure Relief Capability kA - 0,2s||kA||20||20|
|Mechanical Strength: Specific short-term load SSL||Nm||230||230|
- 3542 En-De.pdf Medium Voltage Arresters 10 kA, class 2